ВВГ, ВВГ-П, ВВГнг (А), ВВГ-Пнг(А), ВВГЭ, ВВГЭнг(А), shielded
Conductor: single core «sc» or multicore «mc», or sectoral mould with conductive copper conductor cross-sections from 1.5 mm² to 1000, class 1 or 2 according to GOST 22483-77.
Insulation: (without index) made from PVC-compound, , index ng(A) made from PVC-compound low fire danger. Insulated conductors are color-coded: neutral conductor (N) – blue color, earth conductor (РN) – yellow-green color, please order in advance another color.
Shield: made from copper wire or copper tapes for ВВГЭ, ВВГЭнг(А)
Inner filling and over sheath: without index made from PVC-compound, index ng(A) made from PVC-compound low fire danger Natural coloring with black over sheath , please order in advance another color
Rated voltage, number and conductor cross-sectional area:
|Mark||Number of conductor||Rated voltage, kV|
|conductor cross-sectional area, mm²|
|1||1,5 — 50||1,5-1000||10-1000|
|2 — 5||1,5–240|
Cables are intended for power transmission and distribution on a rated voltage of 0.66; 1 and 3 kV rated frequency 50 Hz for stationary cable lines power equipment.
The cables meet the requirements of GOST 31996-2012 «Power cables with plastic insulation for rated voltages of 0,66; 1 and 3 kV».